Installation and wiring method of DT5 series voltage monitor
- Categories:Installation Guide
- Time of issue:2020-09-30
For DT5/G hanging type series voltage monitor, two-point positioning is adopted.
To monitor the voltage under the outdoor distribution transformer, the meter must be installed in the special terminal box (optional), and then installed under the distribution transformer.
1. Wiring method when DT5 series single channel adopts the first signal and working power supply
The wiring method of the DT5/G voltage monitor with the first signal voltage and working power supply is as follows:
Just connect the first signal voltage to the holes ① and ② of the lower row (XP) wiring holes. If the meter is dual or triple, connect the second signal between ⑤ and ⑥, and connect the third signal between ⑦ and ⑧.
2. Wiring method when DT5/G adopts independent working power supply
The wiring method of the DT5/G voltage monitor with independent working power supply is shown in the figure. In the 8 wiring holes in the lower row (XP), please note that the ③ and ④ pin holes are for the working power supply of the instrument, and the ① and ② holes are connected to the first Road signal voltage. If the meter is dual or triple, connect the second signal between ⑤ and ⑥, and connect the third signal between ⑦ and ⑧.